Since 2001, Emerald Heating & Cooling is your best choice for repair, installation, and service in homes and buildings just like yours in the Erie County. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Emerald Heating & Cooling stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Boiler, and Furnace Repair in Lancaster, NY. Call us today at 716-318-5500!
Installation of new a/c unit was done timely and very professionally. Would recommend.
Jake D was absolutely amazing! He was courteous, knowledgeable and efficient. I will continue to use Emerald Heating because of Jake’s impressive abilities which provided me with an overall impressive experience.
Tech was knowledgeable & professional
Could not have had a better company to work with! Prompt, courteous, explained everything, made sure we saw and understood what they were doing. We highly recommend Emerald!
Justin fixed the issue. We had a new a/c unit installed earlier this week. The air flow seemed weak. Came out within 2 hours of call and fixed the issue. Also reminded me to check the filter and the humidifier screen. Other companies had not shown me how to do this in the past.
Very nice and professional
We called early this morning because our ac unit stopped! Travis arrived just a couple hours later and everything is running beautifully!!
Justin did an excellent job of servicing the A/C and heater in our home. He explained everything as he tested and checked it.
Morgan my installer was a hard working, polite, personable, knowledgeable guy! I’m very pleased with how fast the estimate was done and a/c install. I am so glad that I called Emerald!
Travis provided an excellent explanation of the issues he found during my air conditioning tune up.
He was so helpful and knowledgeable.
We are always pleased with Emerad Heating and highly recommend them to family and friends.
After discussing issues with customer determined to install Uv dye and refrigerant and dual capacitor and humidifier pad, then we will return in two weeks to search for dye using UV bulb. No other issues at this time. Signed up customer for comfort select plan, fee was paid for return charge to look for leak.
Trane Ac and furnace cleaning
Service call water leaking on floor. Problem caused by clogged drain line going to air conditioner.
Amana ac cleaning
Repair AC leak
Discussed with customer options to address potential leak in the system or to just add refrigerant. Customer decided to wait on performing dye test. Installed 2.5 pounds of R410a. Customer is aware for potential leak in system and will address this issue if the same symptoms start to occur again by next year.
Determined system was low on refrigerant. Added 3/4 of a pound to achieve 5 degrees superheat. No other issues found at this time. If issue happens again there is a leak that should be addressed.
Heil furnace repair
Heap Ac install
Test and tune on Goodman AC
No hot water
Bryant ac cleaning
Found bad dual capacitor installed new one, and ensured proper operation.
Determined dual capacitor was bad, still under manufacture warranty not labor warrranty. Installed new one ensured proper operation. No other issues at this time.
Service call weak cooling from Lennox air conditioner.
Completed ac test and tune. No operational issues found at this time. Recomended renewal of comfort select plan for future inspections, declined at this time, will call to renew
Service call water from AC possibly leaking into furnace.
Repair heil air conditioner
Started by checking dip switches on furnace, they where set properly for required airflow for a 3 ton ac system, but was not sending over 150fpm to the registers upstairs. Reset dip switches for a 4 ton ac. 1600cfm, to achieve 350fpm+ out of registers upstairs. Ensured a good 20degree temp drop with airflow change, explained that he may experience some noise from the duct work because of these changes. Customer is going to run it for a week or two and let us know if it is still under performing to his needs.
Completed ac test and tune. No operational issues at this time. System refrigerant level is ok, could maybe use some refrigerant to improve efficiency just not a whole pound. Customer is going to wait at this time.
Rheem furnace inspection
Adam and Brandon are installing a new Amana 2 ton air conditioner
Test and tune on Amana high efficiency natural gas furnace & air conditioner.