In the Erie County, Emerald Heating & Cooling is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Emerald Heating & Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Boiler, and Furnace Repair in Bowmansville, NY in Depew NY. Call us today at 716-318-5500!
I have had Emerald for all my HVAC needs. They are prompt, Professional, courteous. They do a Great job!
I was very impressed with Jim when he came to my home during a problem with my year old furnace. He spent several hours making sure that all was fixed, replaced and tested. I felt very confident that everything was now under control. His professionalism was very appreciated.
Completed furnace and ac test and tune. Furnace has a cracked heat exchanger, inducer motor is slightly noisy, igniter is showing signs of potential failure and ac coil is actively leaking and runs on R22 which is being phased out by 2020. Got Justine out to discuss repair vs replacement of equipment. Discussed add one such as humidifier, WiFi thermostat, and air cleaner, also discussed comfort select plan for future inspections and savings. Declined at this time.
Lennox ac refrigerant check
Lennox ac cleaning
Completed boiler inspection. Also installed 3 new programable thermostats. No operational or visual issues with boiler system. Installed new thermostats because ac would not turn off even if thermostat said it was off. Ensured proper operation of all thermostats. Renewed comfort select plan
Furnace tune up
Rheem air conditioner maintenance
Heil forced air furnace inducer draft motor flame sensor replacement no heat service call
Maintenance Goodman forced air high effecient gas furnace
Fixing a Utica natural gas boiler
Install hot water tank
A/c tune up
Rheem A/C repair
Both upper and lower apartment do not have heat. There is no gas going to the units. Homeowner called the gas company and they're on their way.
Amana 96% forced air furnace two stage natural gas burner variable speed main fan blower. Aprilaire 600 whole house humidifier .
Amana 91% forced air furnace single stage natural gas burner. Variable speed fan blower. Aprileaire 700 Series 120 volt fan powered whole house humidifier.
Lennox 83% efficiency boiler. 112,000 BTU .three zones white Rodgers three-quarter inch one Tayco 007 circulation pump. cast iron air scoop. number 30 expansion tank. 40 gallon indirect hot water tank.
80% Lennox boiler tune up
Found burned out thermocouple on Lennox boiler. Replaced with new
Williams unit heater no heat found dirty contacts at gas control.
Service call (no heat)