Since 2001, Emerald Heating & Cooling is your best choice for repair, installation, and service in homes and buildings just like yours in the Erie County. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Emerald Heating & Cooling stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Boiler, and Furnace Repair in Getzville, NY. Call us today at 716-318-5500!
Excellent. Mark was so helpful in getting all our needs met for heating and cooling issues.
Service call. Determined heat exchanger was breached. Got field supervisor out to discuss repair vs replace. Scheduled new system to be installed on Monday.
Checked heat exchanger for cracks, none found but corrosion is present. Inducer motor pulling proper amount of amps but is noisy. Checked gas valve orphice sand line for leaks found leaks at orphice. Replaced leaking gas valve then rechecked connections with bubbles no more leaks at this time. Showed customer pictures of what the heat exchanger looks like and inducer motor. Also installed two filters, customer supplied. No other issues found at this time but did express concern for possible replacement of inducer motor and heat exchanger in the future.
Before completing test and tune inspection found water in burner compartment due to old hoses having cracks and tears in them. Replaced drain hoses and run capacitor that was getting weak. Continued to test overall operation of system. No other issues found at this time.
Completed furnace test and tune. Recomended starting to consider replacing blower motor due to oil spot, weak capacitor and slow startup. Declined repairs at this time. Unit is 12 years old and may start to experience failures.
Repair blower motor
Test and tune Amana high efficiency natural gas furnace.
Goodman coil pan replacement
Goodman ac leaking water.
Lennox air-conditioning cleaning. System is low on refrigerant. System has a bad compressor. Also the indoor coil is very corroded and leaking into the furnace. Air-conditioner needs to be replaced.
Fixing AC unit capacitor
Repair on AC unit
Repair on Bryant ac
Return trip to check charge
Repair on AC unit
Amanda 96% efficient 100,000 BTU forced air furnace Amana 4 ton air-conditioning single stage compressor R- 410 a refrigerant
Goodman R22 insurance Inspection
Trane air-conditioning cleaning. Replaced two filters. Unit is working properly at this time.
Carrier or stare furnace 100,000 BTU. Single speed fan blower. Single stage natural gas burner. Amanda 3.5 ton air-conditioning single stage compressor R- 410 a refrigerant.
Carrier 82% 100,000 btu forced air furnace. Single speed fan blower. single stage natural gas burner. Amana single stage 3.5 ton R-410a refrigerant. Air conditioning.
Goodman for stair furnace 92% efficient. 80,000 BTU. Single stage gas burner. Single speed fan blower. Heil 3 ton air conditioning. R-22 refrigerant. Single stage compressor.
Trane 80% furnace tune up
Train rooftop Furnace AC package unit 60,000 BTU 80% single stage heat single stage cooling
2 Heil 90% furnace tune ups
No heat. Replaced flame sensor
Furnace tune up