In the Erie County, Emerald Heating & Cooling is well known for providing exceptional furnace repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Emerald Heating & Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Boiler, and Furnace Repair in Getzville, NY. Call us today at 716-318-5500!
Quick and on time
Justin answered all of my questions and addressed all of our needs.
Excellent. Mark was so helpful in getting all our needs met for heating and cooling issues.
Installed new UV bulb and Humidifier panel pad. UV indicator light is now “on” indicating the bulb is good, if light disappears on RGF it is indicating the bulb needs to be replaced again. Humidifier pad should be changed once a year. No other issues or concerns at this time, just recently completed inspections on equipment. Offered csp plan for future inspections and savings on todays bill, signed up for ac inspection next season
Upon completing ac test and tune determined that the system is starting to get low on refrigerant and the dual capacitor is out of tolerance. Static pressure was slightly high, customer supplied new filter. Got Justine out to discuss replacement of the entire system due to being from 2001 and operating on R22 which is being phased out by 2020
Completed 1st year free furnace and ac test and tune. No operational issues at this time. System does have high static pressure causing some noise through the duct work. Humidifier pad needs to be changed before heating season, UV bulb for RGF is bad, gave pricing to replace both items and discussed comfort select plan for savings and future visits. Will be returning august 19th at 8am to install humidifier pad and UV bulb
Repair Lennox air conditioner
Upon completion of ac test and tune, installed new furnace filter and humidifier pad. Static pressure slightly high at .9+ not causing any performance issue at this to,e but could cause excessive noise, we can always address this if it becomes a bigger problem. Overall ac is performing perfectly at this time. Comfort select plan still active to the fall until we inspect the furnace.
Service call. Determined heat exchanger was breached. Got field supervisor out to discuss repair vs replace. Scheduled new system to be installed on Monday.
Checked heat exchanger for cracks, none found but corrosion is present. Inducer motor pulling proper amount of amps but is noisy. Checked gas valve orphice sand line for leaks found leaks at orphice. Replaced leaking gas valve then rechecked connections with bubbles no more leaks at this time. Showed customer pictures of what the heat exchanger looks like and inducer motor. Also installed two filters, customer supplied. No other issues found at this time but did express concern for possible replacement of inducer motor and heat exchanger in the future.
Before completing test and tune inspection found water in burner compartment due to old hoses having cracks and tears in them. Replaced drain hoses and run capacitor that was getting weak. Continued to test overall operation of system. No other issues found at this time.
Completed furnace test and tune. Recomended starting to consider replacing blower motor due to oil spot, weak capacitor and slow startup. Declined repairs at this time. Unit is 12 years old and may start to experience failures.
Repair blower motor
Test and tune Amana high efficiency natural gas furnace.
Goodman coil pan replacement
Goodman ac leaking water.
Lennox air-conditioning cleaning. System is low on refrigerant. System has a bad compressor. Also the indoor coil is very corroded and leaking into the furnace. Air-conditioner needs to be replaced.
Fixing AC unit capacitor
Repair on AC unit
Repair on Bryant ac
Return trip to check charge
Repair on AC unit
Amanda 96% efficient 100,000 BTU forced air furnace Amana 4 ton air-conditioning single stage compressor R- 410 a refrigerant
Goodman R22 insurance Inspection
Trane air-conditioning cleaning. Replaced two filters. Unit is working properly at this time.
Carrier or stare furnace 100,000 BTU. Single speed fan blower. Single stage natural gas burner. Amanda 3.5 ton air-conditioning single stage compressor R- 410 a refrigerant.
Carrier 82% 100,000 btu forced air furnace. Single speed fan blower. single stage natural gas burner. Amana single stage 3.5 ton R-410a refrigerant. Air conditioning.
Goodman for stair furnace 92% efficient. 80,000 BTU. Single stage gas burner. Single speed fan blower. Heil 3 ton air conditioning. R-22 refrigerant. Single stage compressor.
Trane 80% furnace tune up
Train rooftop Furnace AC package unit 60,000 BTU 80% single stage heat single stage cooling
2 Heil 90% furnace tune ups
No heat. Replaced flame sensor
Furnace tune up