Since 2001, Emerald Heating & Cooling is your best choice for repair, installation, and service in homes and buildings just like yours in the Erie County. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Emerald Heating & Cooling stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Boiler, and Furnace Repair in Lake View, NY. Call us today at 716-318-5500!
Jake is a perfect example of a professional. He remembers what happened the last time he came, he knows what to do and does it, he is more than pleasant and efficient. A great worker!
Jake was professional and knowledgeable.
Response from Emerald Heating & Cooling:
Thank you so much for the wonderful review and I am glad we were able to help you out! Have a wonderful day!!
Peerless hydronic boiler
Goodman furnace cleaning
Repair air conditioner
Test and tune furnace and ac
Maintenance amana high efficient natural gas forced air furnace
AC tune up
Furnace AC tune up
Tune up on heil AC
Amana R410-A A/C tune up
Tune up / start up on ac
80% Lennox boiler tune up
90% Heil furnace tune up
Heil furnace cleaning. Replace humidifier pad. Unit is working properly at this time.
TRANE 12 seer A/C maintenance R -22 refrigerant
Amana 96% furnace no heat dirty furnace found to have a bad pressure switch & plugged drain furnace operating fine now after clean out and replace pressure switch
Lennox 80 percent boiler cleaning. Cleaned and checked all boiler operations. Boiler is running properly at this time.
Rheem hi efficient see furnace tuneup found water leak at humidifier feed dirty air filter partly plugged humidifier pad furnace is back to running at its peak performance
Water leak from a goodman 90% furnace. Also found a plugged air filter when testing equipment .